Release notes C2016-02.07.E6
Instability on Citrix servers
We have located and fixed some problems with stability on Citrix servers. This should result in fewer crashes.
Calculation of average heat recovery and SFP values
In the Energy fan we have solved errors in calculation average heat recovery and SFP values when some working points fails calculations.
In alternative working points, it is also possible to type in the percentage of working hours.
Danvent DV and TIME
New IE3 AC-motors
In DV units we have replaced all IE2 AC-motors with more efficient IE3 AC-Motors.
The optimizer can now optimize with all plate distances, for the new H2 plate heat exchanger.
Printout error where units are Approved and shown as approved in Energy fan, but displayed as Failed in printout , have been fixed.
Calculation of Ecodesign values for plate heat exchangers with uneven airflow is fixed.
New Topvex units with counter flow heat exchangers
Topvex TX/C is an air handling unit with top connections requiring minimum floor space. It has a counter-flow exchanger which is normally used when separating supply and extract air is required.
Topvex SX/C is an air handling unit with side connections for minimum build height. It has a counter-flow exchanger which is normally used when separating supply and extract air is required.